Conventional Fire Alarm Control Panel is a 24 volt, four, eight, sixteen-zone, Class B, Conventional Fire Alarm Control Panel. Designed exclusively to meet the latest market requirements and future ULC codes, the highly cost-effective can be used in a variety of low- to mid-sized applications.
*AC POWER:90 to 270VAC, 50 Hz, 3.0 amps.
*Wire size: minimum 14 AWG (2.0 mm2) with 600-volt insulation.
*BATTERY: Sealed lead-acid batteries only.
*Maximum charging circuit: 27.6VDC @ 0.8 amp for normal flat charge.
*Maximum battery charger capacity: 18AH battery.
*Four to Sixteen Style B (Class B) Initiating Device Circuits (IDCs).
*All zones accept two-wire smoke detectors and any normally-open contact devices.
*Zones 1 - 16 configured as general alarm zones.
*All circuits are power-limited and supervised, meeting the latest ULC requirements using fuseless technology.
*Two built-in, Style Y (Class B) Notification Appliance (Signal) Circuits (NACs).
*NACs may be programmed: Silenceable,
*Non-Silenceable, Auto- Silence.
*1.25 amps of NAC power. 3.00 amps of total system power.
*Alarm, Trouble and Supervisory, relay output. 24 volt operation.
*Resettable four-wire smoke detector power @ 500 mA.
*Non-resettable power @ 500 mA.
*Integral battery charger capable of charging up to 18 AH batteries (batteries over 4 AH require use of the external battery backbox, or ULC listed equivalent).
*Disable/Enable control per IDC.
*Reverse polarity protection.