Standalone 433 mhz Wireless Natural Leak Gas Detector Work with Security Alarm System For the Home Security
Remark: 1. The specification of our wireless gas detector is with IC code: 2262, wireless frequency: 433mhz, Timing resistor: 4.7M. This is common specification in the market and can be compatible with all of alarm panels in our store, and most of alarm panels from other sellers. Before buy, you\'d better to check with your alarm panel supplier whether the specification of our wireless gas detector can work with their alarm panel or not to avoid any mistakes. If you don\'t know, please contact us, then we will help you check it.
2. The gas detector can also work standalone. If you just need the gas detector work standalone and needn\'t link with alarm control unit, you needn\'t confirm above specification.
The product is wall mounted gas detector with high stability.(hereinafter called detector) It is used for detecting leaking gas. Advanced semiconductor sensor is adopted to ensure high stability and long life. It is convenient for mounting.The product is suitable for the safety ofresidential house, villas, hotels, markets, boarding house etc.
1. Please note, at present we only have EU and America plug in stock. Please contact us first if you need UK plug.
HIGH RELIABILITY SENSOR
AUTO RESET AFTER ALARM
MCU PROCESSING ADOPTED
AUTO DETECT SENSOR FAILURE
INDUCED GAS- NATURAL GAS / LPG
SMT DESIGN, HIGH STABILITY
Operating Voltage AC100V to 240v
Static Current: less than 90mA
Alarm Current: less100mA
Rating Power: less than 3W
Warm-up Time: about 180S
Alarm Level: 10%LEL
Alarm indicator: red LED flash
Failure Indicator: yellow LED on & beeper long-buzz
Sound Level: more than 85dB/m
Operating Temperature: -10 +50 centi degree
Environment Humidity: less than95% RH (no congelation)
Installation Mode: wall mounted
Alarm Output: relay output/sound & flash alarm
RF 315MHz or 433MHz (wireless type)
wireless Radio Distance: 100m in open area
Outline Size 115*72*41mm
Wireless frequency: 433mhz
IC code: 2262
Timing resistor: 4.7M
Wireless distance: 100m in open area(no obstacle)
Installation of gas detector
Installation should be according to gas weight.
a. For natural gas and mash gas etc, which are a bit lighter than air, gas detector should be installed under ceiling 0.3m to 1.2meters and within the rang of 1.5m semidiameter from gas sources.
b. For liquefied petroleum gas (LPG), which is a bit heavier than air and sink down to a lower level, the gas detector should be installed above 0.3—1.2meters from floor and within the range of 1.5m semidiameter from gas sources